185kw Submersible Pump Farmland Irrigation Stainless Steel
Contact Person : Destiny.Huang
Phone Number : 86 17537187726
WhatsApp : +8617537187726
|Minimum Order Quantity :||1 set||Price :||Negotiable|
|Packaging Details :||Deep well submersible pump is packed by wooden case or as your request.||Delivery Time :||Within 2-5 working days upon receipt of payment|
|Payment Terms :||T/T, Western Union||Supply Ability :||9863 sets per month|
|Place of Origin:||Henan China||Brand Name:||APK|
|Certification:||ISO;CE,BV; TUV; CCC||Model Number:||QJ|
|Voltage:||380v-140v||Power:||250KW 280KW 315KW|
|Frequency:||3 Phase 50hz/60hz||Material:||Cast Iron/Stainless Steel|
|Install:||Vertical||Certificates:||ISO, CE,BV, TUV, CCC|
Sewage Submersible Water Pump For Mine,
Sewage Submersible Water Pump 250KW,
315KW Sewage Submersible Water Pump
250KW 280KW 315KW Sewage Pump For Mine Or Hospital
250KW 280KW 315KW Sewage Pump For Mine Or Hospital Product use:
WQ series sewage submersible pumps are mainly used in municipal engineering, industrial buildings, hotels, hospitals, civil air defense, mines and other industries, and can be used to discharge sewage, waste water, rainwater and urban domestic water with solid particles and various long fibers.
250KW 280KW 315KW Sewage Pump For Mine Or Hospita Conditions of use:
1. The temperature of the medium should not exceed 60°C, the density of the medium should not exceed 1200Kg/m3, and the pH value should be within the range of 5-9.
2. The pump must not be lower than the minimum liquid level during operation, see "minimum liquid level" (including automatic cooling system) in the installation dimension drawing. If there is no automatic cooling system, the minimum liquid level during operation shall not be lower than 2/3 of the total height of the pump.
3. The rated voltage is 380V and the rated frequency is 50HZ. The motor can run normally only when the deviation between rated voltage and rated frequency is not more than ±5%.
4. The maximum diameter of solid particles passing through the pump shall not be greater than 5% of the diameter of the discharge port of the pump body.
5. Seen from the suction port of the pump, the impeller rotates counterclockwise.
Repair and maintenance of 250KW 280KW 315KW Sewage Pump For Mine Or Hospital:
1. The electric pump should be managed and used by special personnel, and regularly check whether the insulation resistance between the electric pump winding and the casing is normal.
2. After each use, especially for thicker and viscous slurries, the electric pump should be put into clean water and run for several minutes to prevent deposits from remaining in the pump and ensure the cleanliness of the electric pump.
3. If the electric pump is not used for a long time, the electric pump should be taken out of the water and not soaked in water for a long time, so as to reduce the chance of the stator winding of the motor getting wet and increase the service life of the electric pump.
4. Under normal conditions, the oil in the oil chamber should be filled or replaced after every 300-500 hours of use of the pump (No. 10-30 engine oil), so as to keep the mechanical seal in a good lubricating state and improve the service life of the mechanical seal.
5. After the electric pump is disassembled and repaired, the casing components must be checked by a 0.2MPa airtight test to ensure reliable sealing of the motor.
6. The seal ring between the impeller and the pump body has a sealing function. If the seal is damaged, it will directly affect the performance of the pump and should be replaced if necessary.
Model of 250KW 280KW 315KW Sewage Pump For Mine Or Hospital: